Power Reactor Event Number: 41616
Facility: SALEM Region: 1
Unit:  [ ] [ ] RX Type:  W-4-LP, W-4-LP
NRC Notified By: STEVE SAUER HQ OPS Officer: BILL HUFFMAN
Notification Date: 04/19/2005 Notification Time: 21:59 [ET]
Event Date: 04/19/2005 Event Time: 20:52 [EST] Last Update Date: 04/19/2005
Emergency Class: NON EMERGENCY 10 CFR Section: 50.72(b)(2)(i) - PLANT S/D REQD BY TS Person (Organization): DAVID SILK (R1)
Unit SCRAM Code RX CRIT Initial PWR Initial RX Mode Current PWR Current RX Mode 1 N Y 100 Power Operation 78 Power Operation
Event Text TECHNICAL SPECIFICIATION REQUIRED SHUTDOWN RELATED TO PRESSURE BOUNDARY LEAKAGE
The licensee "entered technical specification limiting condition for operation 3.0.3 due to pressure boundary leakage on a 3/4 inch pipe on the piping for the boron injection tank.
As a result of this, both trains of high head injection [have been declared] inoperable. Unit shutdown began at 2105 [EDT].
All other safety systems are operable.
Current plans are to take the plant to mode 4 and isolate and replace the affected piping. The current leakage is 780 cc/hr."
The licensee discovered the leakage during operator rounds at approximately 0500 EDT. Technical Specification 3.0.3 was entered at 2052 EDT.
Power reduction is currently in progress.
The licensee will be notifying the NRC Resident Inspector and Lower Alloways Creek Township.